The installation of a wheelchair ramp can mean a better quality of life for you and your loved ones. There are many different ramp options for people with disabilities including portable wheelchair ramps and modular wheelchair ramps. The main consideration if one wants to install a wheelchair ramp is the proper amount of space (length) and elevation (slope). These are both absolutely necessary. Many times it sounds like a viable option, but in reality, lack of space restricts this possibility. While we do not endorse a specific brand or private company, we can put people in touch with individuals who can provide referrals to companies they have used in the past so that you may obtain quotes.
On the Federal side, in terms of financing the project on your own, the Internal Revenue Service (IRS) allows for deductions for certain modifications such as installation of ramps, widening doorways, modifying kitchen cabinets and equipment, moving or modifying electrical outlets and fixtures, fire alarms, and smoke detectors. Accessibility features are considered medical expenses. Check with your local office or tax attorney for details. Your State’s Vocational Rehabilitation program may pay for such things as ramps if the ramp allows a person to get to his or her job.
We also have heard about the non-profit HomeFreeHome.
Started in 2006 on Long Island (NY), HomeFreeHome is a group of volunteer architects who design barrier-free home renovations. Their projects allow people to live with greater safety, dignity and freedom. HomeFreeHome was created to respond to the growing need for accessible housing and increase safe home design for ALL. Over 90% of homes in the United States are not accessible and dangerous. Universal Design enhances the quality of life, regardless of age, or ability.
The Paralyzed Veterans of America also have a great informational book on accessible home design. We included the ADA guidelines for ramps below!
If you have any questions, feel free to contact the Foundation office at 212-955-8727 or firstname.lastname@example.org
Americans with Disabilities Act Accessibility Guidelines (ADAAG)
According to the Americans with Disabilities Act Accessibility Guidelines (ADAAG)
405.1 General. Ramps on accessible routes shall comply with 405.
EXCEPTION: In assembly areas, aisle ramps adjacent to seating and not serving elements required to be on an accessible route shall not be required to comply with 405.
405.2 Slope. Ramp runs shall have a running slope not steeper than 1:12.
EXCEPTION: In existing sites, buildings, and facilities, ramps shall be permitted to have running slopes steeper than 1:12 complying with Table 405.2 where such slopes are necessary due to space limitations.
Table 405.2 Maximum Ramp Slope and Rise for Existing Sites, Buildings, and Facilities
Advisory 405.2 Slope. To accommodate the widest range of users, provide ramps with the least possible running slope and, wherever possible, accompany ramps with stairs for use by those individuals for whom distance presents a greater barrier than steps, e.g., people with heart disease or limited stamina.
405.3 Cross Slope. Cross slope of ramp runs shall not be steeper than 1:48.
Advisory 405.3 Cross Slope. Cross slope is the slope of the surface perpendicular to the direction of travel. Cross slope is measured the same way as slope is measured (i.e., the rise over the run).
405.4 Floor or Ground Surfaces. Floor or ground surfaces of ramp runs shall comply with 302. Changes in level other than the running slope and cross slope are not permitted on ramp runs.
405.5 Clear Width. The clear width of a ramp run and, where handrails are provided, the clear width between handrails shall be 36 inches (915 mm) minimum.
EXCEPTION: Within employee work areas, the required clear width of ramps that are a part of common use circulation paths shall be permitted to be decreased by work area equipment provided that the decrease is essential to the function of the work being performed.
405.6 Rise. The rise for any ramp run shall be 30 inches (760 mm) maximum. 405.7 Landings. Ramps shall have landings at the top and the bottom of each ramp run. Landings shall comply with 405.7.
Advisory 405.7 Landings. Ramps that do not have level landings at changes in direction can create a compound slope that will not meet the requirements of this document. Circular or curved ramps continually change direction. Curvilinear ramps with small radii also can create compound cross slopes and cannot, by their nature, meet the requirements for accessible routes. A level landing is needed at the accessible door to permit maneuvering and simultaneously door operation.
405.7.1 Slope. Landings shall comply with 302. Changes in level are not permitted.
EXCEPTION: Slopes not steeper than 1:48 shall be permitted.
405.7.2 Width. The landing clear width shall be at least as wide as the widest ramp run leading to the landing.
405.7.3 Length. The landing clear length shall be 60 inches (1525 mm) long minimum.
405.7.4 Change in Direction. Ramps that change direction between runs at landings shall have a clear landing 60 inches (1525 mm) minimum by 60 inches (1525 mm) minimum.
405.7.5 Doorways. Where doorways are located adjacent to a ramp landing, maneuvering clearances required by 404.2.4 and 404.3.2 shall be permitted to overlap the required landing area.
405.8 Handrails. Ramp runs with a rise greater than 6 inches (150 mm) shall have handrails complying with 505.
EXCEPTION: Within employee work areas, handrails shall not be required where ramps that are part of common use circulation paths are designed to permit the installation of handrails complying with 505. Ramps not subject to the exception to 405.5 shall be designed to maintain a 36 inch (915 mm) minimum clear width when handrails are installed.
405.9 Edge Protection. Edge protection complying with 405.9.1 or 405.9.2 shall be provided on each side of ramp runs and at each side of ramp landings.
1. Edge protection shall not be required on ramps that are not required to have handrails and have sides complying with 406.3.
2. Edge protection shall not be required on the sides of ramp landings serving an adjoining ramp run or stairway.
3. Edge protection shall not be required on the sides of ramp landings having a vertical drop-off of 1/2 inch (13 mm) maximum within 10 inches (255 mm) horizontally of the minimum landing area specified in 405.7.
405.9.1 Extended Floor or Ground Surface. The floor or ground surface of the ramp run or landing shall extend 12 inches (305 mm) minimum beyond the inside face of a handrail complying with 505.
Advisory 405.9.1 Extended Floor or Ground Surface. The extended surface prevents wheelchair casters and crutch tips from slipping off the ramp surface.
|Figure 405.9.1 Extended Floor or Ground Surface Edge Protection|
405.9.2 Curb or Barrier. A curb or barrier shall be provided that prevents the passage of a 4 inch (100 mm) diameter sphere, where any portion of the sphere is within 4 inches (100 mm) of the finish floor or ground surface.
|Figure 405.9.2 Curb or Barrier Edge Protection|
405.10 Wet Conditions. Landings subject to wet conditions shall be designed to prevent the accumulation of water.